Processing & Handling :: Liquid, Gas and Air Handling :: Steam traps
August 1, 2012
Waterhammer In Condensate Return Lines
Inserting high-pressure condensate into a low-pressure, pumped condensate-return line can cause waterhammer. Understand why and avoid it
Wayne Kirsner Consultant
There is a temptation that steam design engineers find difficult to resist — to put condensate from high-pressure (HP) steam mains directly into the low-pressure (LP), pumped condensate-return (CR) mains. After all, the CR main is so convenient —...
This information is only available to Gold members.
Forgot your user ID or password? Click here to have it sent to you.
Not a member yet?
UPGRADE now to full archive accces and you will receive:
A discount on full delegate pass to ChemInnovations.